230.4V 96AH LiFePo4 Battery Pack For Home Energy Storage System
High voltage 230.4V96AH LiFePo4 battery pack for home energy
22KWH high voltage Energy Storage System Briefly introduction
1,Cell type:32700 3.2V6.0Ah LFP cell
2,Battery box:6 units battery box+ 1 BCU(Battery control unit)
3,Voltage/Capacity Each batery box is 38.4V 96AH(12S16P.6 units
38.4V 96AH connected in series to get 230.4V 96AH.The working
voltage range is 180V-262.8V.The system total energy is 22.1184KWh.
4,Battery system total weight:about 280kg
|1||Battery Pack type||230.4V96Ah|
|3||Max charge current||96A|
|4||Max discharge current||96A|
|5||Cycles life||2000 cycles||25℃±2℃；0.5C discharge and charge rate；80% DOD；|
|6||Cut off discharge voltage||180V||2.5V cut off per series|
|7||Max Charge voltage||262.8V|
|8||Charge and discharge efficiency||≥97%|
|10||Cooling way||Nature cooling|
38.4V 96AH battery module
BCU dimension:2U cabinet
Consider the below points before selecting installation location:
1 There are no flammable or explosive materials
2. The floor is flat and level.
3 Install the system in a visible location so that user can read
the LCD display parameter at any time.
4 The area is completely waterproof
5 Make sure there is 20 cm distance from the two side, 50 cm
distance from bottom of the unit.
6 The ambient temperature is within the range from 0°C to 55°C.
7 The temperature and humidity are maintained at a constant level.
8 The installation areas shall avoid of direct sunlight
9 The distance from air outlet of inverter is more than 0.5 meters.
10 The distance from heat source is more than 2 meters.
11 There is minimal dust and dirt in the area.